The result of computation using MSMAware was checked using spreadsheet in this section.
The proposed of Banglow can be classified as low density development.
According to Chapter 1 of the second edition of MSMA, table 1.1 show the minor design is 5 years ARI for banglow.
The design rainfall calculation method is based on Chapter 2 of the second edition of MSMA.
Determination of Impervious and Pervious Areas
For the purpose of hydrological calculation, the area is shown in Table 5.61.
Table 5.61 Pervious and Impervious Areas
Determination of Time of Concentration, tc and tcs
For catchments of up to 0.4 hectare in area, it is acceptable to use minimum times of concentration given in Table 14.3 of MSMA (2000) instead of performing detailed calculation. The times of concentration adopted are as follows:
- tc= 10 minutes
- tcs= 5 minutes
Determination of Pre and Post Development Flows
The minor drainage system that the OSD storage will discharge has been designed for a 5 year ARI capacity. The rainfall intensity is estimated using equation 2.2 stated in MSMA (2000). Using the Rational Method, the pre and post-development flows are calculated as shown in table 5.62.
Table 5.62 Comparison of Pre/Post Development Peaks for Empangan Sembrong, Johor
For pre development, Qp = 57.69 l/s
For post development, Qa = 104.80 l/s
Determination of Permissible Site Discharge (PSD)
The permissible site discharge (PSD) for the site is calculated using equation 19.1 with equation 19.1c and equation 19.1d for below ground storage. The results are tabulated in Table 5.63.
Table 5.63 Computation of Permissible Site Discharge (PSD) for Empangan Sembrong, Johor
Determination of Site Storage Requirement (SSR)
Using equation 19.2 with equation 19.2c and equation19.2d for below-ground storage, the site discharge for the storage design storm (10 year ARI) and the corresponding SSR is calculated for range of storm duration to determine the maximum SSR. These calculations are summarized in table 5.64 and 5.65.
Table 5.64 Computation of Peak Post-Development for Empangan Sembrong, Johor
Table 5.65 Computation of Site Storage Requirement (SSR) for Empangan Sembrong, Johor
Required PSD = 74.41 l/s
Required SSR = 51.75 m³
Editor :- Dilah – 31 March 14